Data Center Infrastructure:
MultaHost Data centers offer complete redundancy in power, HVAC, fire suppression (FM-200), network connectivity and security, incorporating raised flooring (DC1 & DC3), dual power grids, UPS battery backup power and diesel generators. Two primary MultaHost Data Centers are located on the 4th floor of 707 Wilshire Blvd. in downtown Los Angeles, This location enables us to connect easily to virtually any backbone provider and scale our internet connectivity to meet client's needs. Additionally the Network is directly connected via diverse path Fiber Optic lines to many of the other carrier buildings in downtown such as One Wilshire and 818 W. 7th which host our network equipment. Services offered at these data centers include private caged suites, cabinets, half-cabinets and rack space. Data centers are continuously monitored via video surveillance cameras and 24 hour on-site security personnel. With use of sophisticated two-tier access control systems, access to 4th floor, elevators as well as the Data centers is restricted and controlled via HID contact-less access control system. Video is stored in secure room at Data center 3, two miles east of this location.
True 2(N+1) Design, step higher fault tolerance then N+1 offered by most other data centers. Power is provided via two active feeds from two power busses which are connected to separate and independent Diesel Generators and finally backed up by two redundant UPS systems. In addition to the most fault tolerant system in both data centers, Data center 1 (Suite 405) also has an additional power source with its own UPS backup system providing divergent power supply.
Data center 1, 110V, 220V and 48V DC Power can be provisioned.
Data center 2, 110V 20A Circuits.
Data center 3, 110V and 220V 15A, 20A, 30A Circuits.
Both data centers employ redundant set of 11 HVAC systems which are controlled by an automated software. One set of the HVAC units (Primary Set) utilizes building chilled water and the other set (Secondary Set) utilizes dedicated chillers which are on the side of the building and are independent of buildings chilled water supply.
The location uses diverse conduit paths to many other carrier buildings in downtown Los Angeles. Minimum of 192 strands of dark fiber between each connected building and divergent path to many of the carrier buildings ensures unsurpassed network reliability at this location.